Author Message

Joined: 07 Jan 2010
Posts: 173
Location: Yorkshire,
United Kingdom
Thanked: 1 time

 Posted: Sun Jan 17, 2010 5:51 pm Could someone please explain the relationship between water pressure and flow rate. For example, assuming the cold water feed into a house is split and fed in parallel through a 22mm pipe and a 15mm pipe of the same length, what is the relationship between the pipe diameter, pressure and flow rate. Are the following statements correct: The water pressure will be higher in the 15mm pipe as it is of a narrower diameter. The flow rate will be the same in both pipes as that is dependant on the flow rate of the mains cold water supply and isn't affected by the pressure. If a 10 litre bucket was placed under the open end of each pipe, then I assume they would both fill at the same rate, despite one pipe forcing the water out at a higher pressure than the other. As the mains pressure is increased or decreased, the pressure in both pipes would increase or decrease. What would happen to the flow rate? Similarly, if the mains flow rate is increased or decreased, the flow rate in both pipes would increase or decrease. What would happen to the pressure in the pipes? Thanks in advance.

Joined: 15 Dec 2006
Posts: 4488
Location: United Kingdom
Thanked: 555 times

 Posted: Sun Jan 17, 2010 6:16 pm Pressure is fairly constant, as provided by the local water company. Flow rate will be better with larger bore pipework (less restriction) http://www.ehow.com/about_5533714_water-flow-vs-pressure.htmlLast edited by baxpoti on Sun Jan 17, 2010 6:26 pm, edited 1 time in total

Joined: 28 Oct 2005
Posts: 5290
Location: Oxfordshire,
United Kingdom
Thanked: 758 times

 Posted: Sun Jan 17, 2010 6:25 pm Google Bernoulli's Principle

Joined: 07 Jan 2010
Posts: 6
Location: Oxfordshire,
United Kingdom
Thanked: 1 time

 Posted: Mon Jan 18, 2010 12:43 am Get yourself a large diameter cylinder 10 metres long. Stand it on end and fill it with water. If you measure the pressure at the top just under the water level it will be nothing (nothing above atmospheric pressure) Go to the bottom and the pressure will be one bar above atmospheric. Now stick 1 metre lengths of 15mm and 22mm dia pipe horizontally out the side of the cylinder at the bottom. If you put a bung in the end of each pipe and measure the pressure at the end of either pipe it will be the same, one bar. No water is flowing so we just measure the static pressure. Now pull the bungs out. If you measure the water pressure at the bottom of cylinder it will be one bar still. The pressure at the open end of the pipe will be close to atmospheric. Water is being pushed down the pipes by that one bar difference between the pressure inside the cylinder and atmospheric pressure outside. The 22mm dia pipe is more than twice the cross section of the 15mm dia pipe so its bucket will fill more than twice as fast. If you went and got a 20 metre long cylinder and did the same thing the pressure at the bottom would be two bar. The pressure difference pushing water along the pipes would be twice as much and roughly water will flow twice as fast. The bucket under the 22mm pipe will still fill twice as quickly as the bucket under the 15mm pipe
 The following user says thank you to David0123 for this useful post: ChilliChowder (10 Feb 2014) Alert Moderators

Joined: 20 Oct 2008
Posts: 67
Location: United Kingdom
Thanked: 7 times

 Posted: Mon Jan 18, 2010 10:03 am Many thanks to David for explaining that in simple terms. Very useful. Even I could understand it.
 All times are GMT Page 1 of 1

 Jump to: Select a forumForum InformationOffers & Discount CodesYour ProjectsDIY DisastersTrade TalkHobbiesGeneral DiscussionWord GamesJokes ArchiveAlarms, CCTV & TelephonesAppliancesAudio VisualBuildingBuilding Regulations and Planning PermissionDecorating and PaintingElectrics UKElectrics Outside of the UKFloors, Stairs and LoftsIn the GardenPlastering and RenderingPlumbing and Central HeatingRoofing and GutteringTilingTools and MaterialsWindows and DoorsWood / Woodwork / CarpentryGeneral DIYGeneral CarsCar Repairs / MaintenanceSoftwareHardwaretestYour test
You cannot post new topics in this forum
You cannot reply to topics in this forum
You cannot edit your posts in this forum
You cannot delete your posts in this forum
You cannot vote in polls in this forum
Similar Topics   Replies   Views   Posted
Explanation Please, boiler losing pressure (maybe fixed) 9 120 Fri Jan 13, 2012 7:00 pm
Potterton PUMA 100 - must be a simple explanation? 2 1020 Sun Feb 29, 2004 11:45 am
Is there an obvious explanation to boiler problem? 10 380 Wed Apr 15, 2015 7:30 am
Shower Fire - Explanation Needed 13 400 Sat Jul 09, 2011 7:28 am
Boiler schematic explanation 37 8680 Thu Dec 13, 2007 8:12 pm

 DIY | DIY How To | @home | DIY Wiki | DIY Forum