Unnecessary , what happened to isolating.
The seal at the end connecting to the pan should be inwards
Obviously aware of that. was responding to comments regarding having it serviced and then issuing a gas safety record
Tightness test not legally required for landlord cert. You can buy a u gauge to test gas but do you know about letby , temperature...
Dan. Don't be a p you might need a sock off Jeff. In the cc
Dan I am well aware of what needs to be checked at the meter on a install. My point was that the meter is external and could have been tampered with.
Who's to say that the rgi left it off. The meter box is external
So you have had a trouble free 5 years and now it's a terrible boiler
Keep the boiler and sack the engineer. Looks like leak on diverter. Parts are available
Upstream /downstream, when connecting, reverse when disconnecting
Grouch, enjoyed his post in cc, think he ****ed off some knob heads in general forum
Increase heigth of cold water storage cistern in loft
The post was in jest, you have had advice on here from some very knowledgeable plumbers/rgi.
Put it very high up in the loft, vent by taking cap off and depressing schrader valve
1"1/4 waste pipe and solvent weld fittings
Separate names with a comma.