It was (In my opinion) established back in post 13 by chunky that it is a voltage trip. What has not been proven is that it is still functioning...
Best you look up what the term means in that contex then.
You are correct, 1mm2 is all that is required.
Work safely now!
You need a Home Office Shield, Google Hager Home Office Shield. Cost pence.. There are dozens of shades that will fit a standard Batten holder.
See post 34 !
Jolly good, now relax and give your gf a hug.
If you have it connected as in post on. 5 then as has been asked is the programmer/ timer calling for heat? ie. Set to perm on or 24hrs.
OK just wanted to be sure that red was in third hole. Yel in 4
Hi Show us a better pic of no.2 so we can be sure which cables are in which holes, it's not obvious at the moment.
As it's all on a single Tarrif (24hr) it should never have been left as a dual set-up. I agree it wants the consumer unit correcting to reflect...
PME is a 5min job once they have ascertained the network is suitable, most are. You have what appears to be a TN-S Earth there, if that has been...
Ive only ever seen dual taraff boards with two Main Switches BUT labled as such. No different to having two cu for whole installation. On peak and...
If you want PME then it's up to the DNO to supply it, your electrician cannot do it.
As you have no storage heaters, have the points been converted to 13A sockets? If so then maybe the consumer unit has been doctored to reflect this.
In the past it was always the consumer that was responsible for their earthing. If the distributor offered a earth terminal you can/should use it.
Here we go.......
You suspect correctly, It's a Dual Tarrif board.
Exactly, should have ticked 1 phase (two wire)
Single phase 3 wire, often found in rural areas, farms etc. Fed from single centre tapped transformer. Giving two lines + neutral (180 degrees...
Also 1phase (3 wire)?
Separate names with a comma.