Try pressing the reset, X button below the 7.
Also, from the picture it looks like the alarm is already set. There should be a green light underneath the unlocked padlock symbol, next to the...
The red light indicates that the alarm is receiving mains power. It should always be on. Unless there is a power cut.
What have you done to try...
If you would like to link out the tamper for the bell box you'll need to look for the bell box connections near the right hand side of...
You're welcome mate . Make sure you've tested the bell and strobe. Any more problems let me know. Cheers
Hi. Connect siren up with alarm panel powered down. Make your connections and power up again.
Wire up as follows:
(Siren - Panel)
TR ------- T
S --------- B
V+ ------- D
V- -------- A
ST ------- Strobe -
Hope this helps.
Do you know the make/model of the sounder?
Ok mate. Glad it's sorted
No problem mate. Glad it's sorted.
Hi, sorry for the confusion. Its the terminals at the bottom of the panel. Left hand PA and SET.
It's worth a try. If not the panel is defective....
That is odd.
Seems like the engineer code has been changed.
Try defaulting panel to factory settings:
1. Power down panel.
2. Remove wiring...
Sounds like the zones are disabled via the engineering program for Program 1.
Do you have the engineer's code? -factory default is 9999.
Wire blue and white into the TAMP terminals (doesn't matter which way round).
Wire green and yellow into Zone 1 (doesn't matter which way...
Have you not thought about using the keypad's built-in panic button (buttons 4 and 9 simultaneously) ?
You cannot wire directly to the...
Your welcome, hope it gets sorted.
Hi SCB is for the alarm bell box outside.
The two terminals are linked by default as they provide tamper protection for the bell box. Take the...
Set up P1 as normal to protect house and outbuildings then you could either disable the lounge zone on P1 permanently...
Thought 15v was unusual.
Separate names with a comma.