Author Message

Joined: 03 Feb 2010
Posts: 3
Location: London,
United Kingdom

 Posted: Wed Feb 03, 2010 9:51 am Hi, I was wondering if anyone knows where I can get a table with information on different gas meters and their capacity (in cubic meters)? I have an existing R5 meter (which as far as I understand is imperial and rated in cubic feet) but am not sure what the actual capacity of this meter is? I am looking to install some new plant (boilers, CHP, direct fired DHW heater) and am sure that the meter will need to be upgraded. One other point is that the existing supply seems to be around two inches. Thanks!

Joined: 12 Nov 2008
Posts: 684
Location: Tyne and Wear,
United Kingdom
Thanked: 61 times

 Posted: Wed Feb 03, 2010 11:37 am Most domestic gas meters are rated at 6 cu mtrs/hr. or in your case imperial 212 cu ft/hr. which converts to 6 cu mtrs/hr. The capacity you should be able to see printed on the dial/read out.The R5 refers to an index which has an output pulse which can be used for on site data logging or remote modems. Generaly domestic meters are refered to as U6(mechanical) E6(electronic) =6cu mtrs/hr. Depending upon your requirement you may need a U16 =16 cu mtrs/hr. The sizing of the meter requirement involves a modecum of complicated maths based on all of the appliances input or outputs and will be done by the gas transporter, who is responsible for the meterLast edited by snugib on Wed Feb 03, 2010 11:50 am, edited 1 time in total

Joined: 03 Feb 2010
Posts: 3
Location: London,
United Kingdom

 Posted: Wed Feb 03, 2010 11:47 am Thanks for the reply although I am still slightly confused abotu how I can work out the size of the existing meter. The only numerical markings on the meter are R5. Does this correspond exactly to the U scale? For example an R5 = U6, R6 = U7...!? I have found a manufacturer that supplieda number of different meters and there are q few different sizes with different letters such as: G1.6 / G4 / G4P / U6P / E6 / SC6 / G6 / G6P / G10 / U16 / U25 / U40 / U40P / G40 / U65 / U100P / U160P What does the G, P and E stand for in these sizes and how does it all relate to the U sizes and R sizes? Thanks a million!!

Joined: 12 Nov 2008
Posts: 684
Location: Tyne and Wear,
United Kingdom
Thanked: 61 times

 Posted: Wed Feb 03, 2010 12:17 pm Look very closely at the meter index the capacity must be printed on it, usually in very small print (can you post a pic) All those model types you quoted, all you are interested in is the digits ie from 4 to 160 cu mtrs/hr. Not sure what all of the letters mean, maybe some manufacturers id. I do know the U means mechanical mechanism (diaphragm) and E means electronic mechanism ( sensors that look at time of flight in the gas stream) The R5 has nothing to do with capacity, it just means that the index provides a pulse switched output that can be used for on site data logging

Joined: 12 Nov 2008
Posts: 684
Location: Tyne and Wear,
United Kingdom
Thanked: 61 times

 Posted: Wed Feb 03, 2010 7:32 pm Typical example

Joined: 03 Feb 2010
Posts: 3
Location: London,
United Kingdom

 Posted: Wed Feb 03, 2010 7:59 pm Thanks for your help!

Joined: 25 Mar 2010
Posts: 1
Location: United Kingdom

 Posted: Thu Mar 25, 2010 8:05 am hi is this a unit factory or a house with a 2inch service its normally a factory unit looking at that meter i would say its a u6 as to calculating the size of meter you would need to find out how much gas your new appliances and existing appliances will need you gas network or supplier woul beable to help

Joined: 23 Nov 2011
Posts: 5
Location: Manchester,
United Kingdom

 Posted: Sat Jun 09, 2012 7:17 pm Betacom 24 combi boiler glow worm,radiators not getting hot!,the boiler fire's up,the hot water side works fine!,checked the operation of the pump the impeller rotates on all three speeds,but very hot to touch,also found a small leak on the back of the 3 way valve,can any one advise me on the fault and give me remedy.

Joined: 08 Oct 2011
Posts: 6277
Location: Hertfordshire,
United Kingdom
Thanked: 988 times

 Posted: Sat Jun 09, 2012 11:44 pm WTH has this got to do with gas meters?

Joined: 02 Nov 2011
Posts: 762
Location: Cheshire,
United Kingdom
Thanked: 60 times

 Posted: Sun Jun 10, 2012 12:23 pm I think he might be implying that its BGs fault...

Joined: 10 Jun 2009
Posts: 5107
Location: Suffolk,
United Kingdom
Thanked: 971 times

 Posted: Sun Jun 10, 2012 3:39 pm Sudds would do better if he/she opened their own and NEW THREAD!!
 The following user says thank you to Boilerman2 for this useful post: BGSMJack (10 Jun 2012) Alert Moderators
 All times are GMT Page 1 of 1

 Jump to: Select a forumForum InformationOffers & Discount CodesYour ProjectsDIY DisastersTrade TalkHobbiesGeneral DiscussionWord GamesJokes ArchiveAlarms, CCTV & TelephonesAppliancesAudio VisualBuildingBuilding Regulations and Planning PermissionDecorating and PaintingElectrics UKElectrics Outside of the UKFloors, Stairs and LoftsIn the GardenPlastering and RenderingPlumbing and Central HeatingRoofing and GutteringTilingTools and MaterialsWindows and DoorsWood / Woodwork / CarpentryGeneral DIYGeneral CarsCar Repairs / MaintenanceSoftwareHardwaretestYour test
You cannot post new topics in this forum
You cannot reply to topics in this forum
You cannot edit your posts in this forum
You cannot delete your posts in this forum
You cannot vote in polls in this forum
Similar Topics   Replies   Views   Posted
Table Y tube. 3 600 Sun Nov 04, 2007 12:25 pm
Table-top dishwasher HELP please!!! 5 440 Mon Jul 19, 2010 1:47 pm
Table top dishwasher - plumbing advice please! 5 660 Mon Apr 07, 2008 4:32 pm
LPG Gas Flow rate discharge table. 15 140 Mon Sep 19, 2011 10:20 am
Need help finding a table of thermal lateral pipe expansion? 6 80 Sun Oct 21, 2012 4:42 am

 DIY | DIY How To | @home | DIY Wiki | DIY Forum