Author Message

Joined: 18 Sep 2005
Posts: 92
Location: Ayrshire,
United Kingdom

 Posted: Thu Oct 06, 2005 6:30 pm Hi Can any of you explain, or recommend sites that can explain earth loop impedance, the theory & testing? I never got the hang of it during my day release classes which was many years ago. BTW this a great site, only found it a couple of weeks agop.

Joined: 18 Jul 2004
Posts: 7708
Location: Devon,
United Kingdom
Thanked: 306 times

 Posted: Thu Oct 06, 2005 6:47 pm Resistance from the live to earth, via the supply cables and transformer. Using ohms law, you can determine the fault current in amps, that would flow if a dead short was introduced. This is the current that would flow down the earth to the substation, and back up the live to your fuse, as the fuse blows. The lower the earth loop, the higher the PFC (prospective fault current). The higher the PFC, the quicker the fuse will blow. We need to therefor know the earth loop (Ze at origin, Zs at circuit end) to determine weather the fuse/mcb will operate quickly enough to give disconnection with in the time stated in regs (0.2, 0.4 or 5 seconds, depending on circuit type and location). A TN-S or TN-C-S system will give nice low resistances, the REC state that for a TN-S system, the max Ze they will provide will be 0.8ohm. For TN-C-S it will be no more that 0.35ohm. For a TT system, the earth rod will generally give a higher resistance, and therefore will not provide a high enough fault current to operate the fuse/mcb quickly enough to conply to the regs. This is why on TT systems, an RCD is essential.

Joined: 18 Sep 2005
Posts: 92
Location: Ayrshire,
United Kingdom

Posted: Thu Oct 06, 2005 7:15 pm

Thanks for the speedy response.

 Lectrician wrote: Resistance from the live to earth, via the supply cables and transformer.

Can you explain further - how is the resistance between the live and earth measured? Should this resistance not be at infinity or very close to it?

Joined: 11 Jan 2004
Posts: 25670
Location: Cheshire,
United Kingdom
Thanked: 473 times

 Posted: Thu Oct 06, 2005 7:21 pm I know you - you're Lionel's brother - Maballsa Ritchie!

Joined: 27 Aug 2003
Posts: 50528
Location: London,
United Kingdom
Thanked: 1969 times

Posted: Thu Oct 06, 2005 7:26 pm

 Maboza-Ritchy wrote: Can you explain further - how is the resistance between the live and earth measured? Should this resistance not be at infinity or very close to it?

You might be saying that because you missed a word out of your question.

Earth Fault Loop Impedance.

You want to know what the impedance will be if you were to get a L/E fault, because if it is too high then the protective device will not operate quickly enough. This is a Bad Thing™.

Re sites - try these:

http://www.tlc-direct.co.uk/Book/5.1.1.htm

http://www.tlc-direct.co.uk/Book/8.1.1.htm

Joined: 18 Sep 2005
Posts: 92
Location: Ayrshire,
United Kingdom

Posted: Thu Oct 06, 2005 9:06 pm

 securespark wrote: I know you - you're Lionel's brother - Maballsa Ritchie!

Your right! Maboza is the scottish equivalent of Maballsa. It's the same as Tom and Tam, Willie and Wullie etc.

Joined: 18 Sep 2005
Posts: 92
Location: Ayrshire,
United Kingdom

 Posted: Thu Oct 06, 2005 9:19 pm Ban Thanks for the reply and link to the site. I'm going to hit the sack (early bedder) for now but will it check it out tomorrow. Thanks again for swift reply. Ciao Maboza (Maballsa)

Joined: 12 Jul 2005
Posts: 776
Location: Bedfordshire,
United Kingdom
Thanked: 5 times

Posted: Fri Oct 07, 2005 7:18 am

This thread reminds me to ask a question that i've been wondering for a while. It's an out of interest thing only...

 Quote: the REC state that for a TN-S system, the max Ze they will provide will be 0.8ohm

If your TN-S Ze is > 0.8 ohm, are the REC obliged to fix it, or can/will they just re-designate it a TT supply and leave it to the customer to get an earth rod & RCD ?

Joined: 18 Jul 2004
Posts: 7708
Location: Devon,
United Kingdom
Thanked: 306 times

 Posted: Fri Oct 07, 2005 2:55 pm They are not obliged to provide an earthing terminal. So if it involved excessive re-cabling, and not locating a high resistance joint (for example), I think they would remove their earth terminal, and tell you to sort your own!!
 All times are GMT Page 1 of 1

 Jump to: Select a forumForum InformationOffers & Discount CodesYour ProjectsDIY DisastersTrade TalkHobbiesGeneral DiscussionWord GamesJokes ArchiveAlarms, CCTV & TelephonesAppliancesAudio VisualBuildingBuilding Regulations and Planning PermissionDecorating and PaintingElectrics UKElectrics Outside of the UKFloors, Stairs and LoftsIn the GardenPlastering and RenderingPlumbing and Central HeatingRoofing and GutteringTilingTools and MaterialsWindows and DoorsWood / Woodwork / CarpentryGeneral DIYGeneral CarsCar Repairs / MaintenanceSoftwareHardwaretestYour test
You cannot post new topics in this forum
You cannot reply to topics in this forum
You cannot edit your posts in this forum
You cannot delete your posts in this forum
You cannot vote in polls in this forum
Similar Topics   Replies   Views   Posted
Earth loop impedance on TT? 13 900 Sun Mar 19, 2006 8:40 pm
Earthing Supply Type help -High Earth Loop Impedance reading 35 740 Wed Jul 11, 2012 12:40 pm
Earth Fault Loop Impedance 7 1680 Sun Jun 17, 2007 12:27 pm
Earth fault loop impedance test (Ze) with Multimeter? 31 1360 Mon Apr 21, 2014 1:39 am
High Earth Fault Loop Impedance on TN-S (106ohms) 11 3960 Mon Mar 09, 2009 8:01 pm

 DIY | DIY How To | @home | DIY Wiki | DIY Forum