I'm sure you can get ones with an led strip all the way round..
there are minimum clearances and so on..
plasterboard lining with fire hoods and a fan for ventilation?
To clarify.. the switched live at the fan should be the one that's on when the light is on, the other one is the one mentioned above..
It's the switch end..
take the one which is suppose to be permanently live and connect it to the one in the switch that is permanently live.. (...
Provided ther are the same size yes..
Wouldn't a double pole switch get rid of this?
Break the neutral and no current flow.
But that involves re-wiring probably.
It's been a while since I've peeked at the regs but I thought that fire rated were only needed in a ceiling used as a fire barrier such as a...
Several alarm bells rang on reading that first post..
1:- "?.. issue with THE socket circuit..." .. there should be at least 2.. upstairs and...
Ah.. I've found the PDF..
turn the switch off..
The humidity is automatic with the switch OFF
Turning ON the switch turns on the fan which runs...
Is there a setup time for the humidity stat? What do the instructions say?
The old extractor had a permanent AND switched live but no timers etc?
The browns in the crimp should be the permanent live,...
Could be the beam angle?
Are the replacement ones reflector type?
4 way wago connectors? ( 1 in, 3 out )
Safety's by means of placing out of reach.. ?
Irrelavent as to what "the norm" is in your opinion.. the OP asked about de-rating, not "rule of thumb" circuit design.
If you need to use 1.5mm...
Separate names with a comma.