Tony my boiler has been serviced by a good gas engineer everything was 100% (not installer) an tested 98% efficent i have also have it booked for...
thats why your the plumber im the customer chap
nothing is ever 100% accurate i got 10ltrs 45 degC 52sec =12ltrs every 1min 4secs hardly life changing
since i have have 5 yr warranty going to...
outside tap 10ltrs 42sec
but thats one off them b&q clamp on fittings so restricted flow anyway
do you think what my boiler is doing is normal regardless of brand lol i said the C/H side perfect no problem this far
i def ain't mathmatically minded lol
but i set the boiler to 45deg with tap full open it reach 42deg even if i move the dial up to 50 deg the...
please tell me if i did this right
i set my boiler to 55 degrees turned tap on full boiler reached 39 degrees no more
while at that temp filled...
definatly going down the right pipes
the boiler light lights up an stays lit till tap off
thats with the boiler a 58 degrees on the switch...
i have a fernox f1 which i had cleaned an the fernox system cleaner an renewed inhibitor when i installed new radiator in the...
right guys i want no wise cracks plz
i have a problem concerning my combi boiler wait for it "ideal logic +30" so i know what your going to...
right chaps haven't had a chance to see your comments till now
the spark had it wired to ebus so today i unwired the 2 switch wires from the...
believe me have no intention waiting 2 weeks
Separate names with a comma.