All those that consider working live to be acceptable should go and read Regulation 14, and then explain in detail how their live working complies...
Likely causes are the plastic tray on top of the compressor is loose, or one of the rubber mountings for the compressor has disintegrated.
It was a regulation, so was the maximum floor area and several other things.
Now it's all in the appendix, which is not...
The Wylex fuseboxes were either rated for the same in each way, with a maximum of 30A.
A few were made with one way suitable for higher current,...
Despite what many people think, circuit breakers are not indestructible and most definitely have a limited lifespan.
Other manufacturers will be different.
Another important consideration is whether the MCB will be fully loaded during normal use.
What is the fuel source for the Aga?
It doesn't have 3 outputs. There are 2 wires in for the supply, and 2 wires out for whatever is connected to it.
Assuming it's working,...
That is a current operated device, and does the same thing that a modern RCD does. It is not one of the voltage operated devices which have been...
Surge protection devices (SPDs) are not filters.
They only react to high voltage transients, and won't do anything at normal operating voltages.
Which 'unit' are you referring to?
There are no plugs - the cable is connected directly to the socket....
CEF have both 3m and 3.75m
No idea where you got those from, but it's totally wrong.
The correct wiring:
A big slab of grout is the only option.
Too late now - but bevel edge tiles are really not a suitable choice where electrical accessories are to...
Separate names with a comma.