Hopefully this is safe and within regs, just a check for peace of mind - from a bedroom double socket I've taken a 2.5 T&E spur which goes to a 13amp switched FCU in the loft. From this FCU load I have two 2.5 T&E cables, one goes to a single socket in the loft which then runs to a double socket in another loft. The other 2.5 T&E cable runs to another switched FCU, which is fused down to 5 amp, and from this runs 1.5 T&E to a light in the loft (the switch on this FCU is the switch I use for the light). Therefore the light is fused down and this as well as both sockets are protected by the 13amp FCU. My only two unsures are - am I ok to take two cables from the FCU load or is there a reg which states there can only be one, and should the fuse for the light really be 3amp. Thanx.