It was agreed that the original tails would be removed and replaced with longer, continuous cables. There shouldn't have been connector blocks.They will need access for maintenance/testing for sure. They appear to be floating in the air at present? Red Black single insulation?
Is this the only place they could have gone? Is it close to where the DNO cut out is? How far? Where's the Meter with regards to this?
If you count the cables into the photo and the cables out of the photo it looks suspiciously like a "joint" (the cable connection type)Is there a certificate for the consumer unit install / move?
Maximum length of tails is usually 3m.
Tails cannot be concealed in the wall unless more than 50mm from the surface.
The black/red wires look to be smaller than the grey ones - should be the same size.
Also have to ask where these came from, as such colours haven't been available for well over a decade.
Connections must remain accessible, and those black connector boxes must be securely fixed to something, not left hanging on the wires.
What is this taped up mess?
View attachment 151522
If you need to find a tradesperson to get your job done, please try our local search below, or if you are doing it yourself you can find suppliers local to you.
Select the supplier or trade you require, enter your location to begin your search.
Are you a trade or supplier? You can create your listing free at DIYnot Local