He must be Eddie Boulter the Second!!!
Hi Guys, my oil fired Trianco Eurostar 50/90 external boiler was locking out and I spoke to a service man who told me that there is a known issue with this type of boiler -- it needs a low air mixture. I had it set by a man with a meter and he set the air slide at 9.8, (max setting is 15). Boiler locked out regularly, sometimes on first start other times after cycling off and on. I set the air back to 5.3 and it doesn't smoke and doesn't lock out. One other curious point which I welcome some advice on is this ---- in order to assure proper firing I had to extract the photo cell about 1 cm from its holder and rotate it 20 degrees anti clockwise. With the low air setting at 5.3 and the photocell extracted slightly the boiler works great.
(tonight I pushed the photocell back in and the boiler locked out).
Any opinions would be welcomed.
I wrote to Trianco but got no reply!!!
Just one last point, have you noticed any re-ignition during the boiler running times?
If you need to find a tradesperson to get your job done, please try our local search below, or if you are doing it yourself you can find suppliers local to you.
Select the supplier or trade you require, enter your location to begin your search.
Are you a trade or supplier? You can create your listing free at DIYnot Local